From: Troy Monson
Company Name: Ziegler Caterpillar
Email: troy.monson@zieglercat.com
Phone: 5153147040
Project Size: Small
Project Description:
Generator Enclosure Request for Caterpillar C32-1250 
Please let me know if you are interested and if/when in 2023 you have production slots. Will need quick turnaround on this proposal.  
OPTION A
175mph Wind Rating (Will be put in Florida Hurricane Zone A)
5000 Gallon U.L 142 Sub Base Tank with FDEP (Florida Department of Environmental Protection)
PE Stamped Drawings for the State of Florida
Aluminum Panel Construction (marine environment) with powder coat exterior
Fuel tank to have additional rubberized undercoat
Use your equivalent as necessary
I have the engine in stock 
Weather protective enclosure
•            3" .125 Aluminum panel construction
•            Enclosure frame 6" Tall (Designed to remove entire enclosure for major service) Lugs only provided Per customer request or when enclosure ships to site separate
•            Pitched Roof construction W/ Safety Lanyard tie off eye's spaced across entire roof
•            Powder Coat Paint exterior Caulked seams
•            Roxul 4lb UL Listed Acoustic/Thermal Insulation
•            22GA Galvanized perforated interior liner
•            Standard doors 36"W x 72"H
•            Standard Door hardware with pad lock/key lock and hinges
•            Stainless Steel spring loaded door hold back on every door
•            Dripedge above all door openings
•            Exhaust hardware for enclosure mounting
•            Drip edge around exhaust opening (rain shield)
•            Aluminum Gravity Radiator air discharge dampers
•            Radiator vertical discharge air plenum W/ Screen & 1 Access Door
•            Aluminum Fixed intake louvers W/ Screen
•            Document holder mounted inside enclosure
•            Supply critical grade (Internal mounted) silencer & exhaust system 120/240V 100A Load Center W/ Main breaker & branch breakers
•            (4) LED vapor tight lights W/ Guards (Includes: 2 GFCI receptacles & 2-3 way light switches)
•            4) Enclosure Doors (Two Per Side of Enclosure)
•            IBC and Seismic Signed & Approved Drawings by a PE for the state of Florida where the generator package will be installed Stainless Steel Door Hardware & Hinges
•            Stainless Steel Exterior Hardware
•            UL 142 Secondary containment sub base tank
•            Heavy gage side channels
•            Mechanical Fuel level gauge
•            UL/NFPA sized emergency vents
•            2" Standard working vent W/ Screen & Rain Cap
•            Low fuel level alarm (50%)
•            Manual locking fill cap
•            Rupture Basin alarm
•            Lifting plates (2 Each Side-Min.)
•            Prime and finish painted black) Electrical stub up area
•            90% High Level Alarm
•            Mount Generator on Fuel Tank
•            Standard Fuel Lines
•            2" Quick Connect on fill port W/ Dust Cap
•            2" 95% Overfill Prevention Valve on fill port
•            24V DC High Fuel Alarm Box W/ 90% Full Level Horn, Horn Re-Set Switch & Reset Float Switch
•            (2) 2" NPT Spare Fittings
•            Extend normal vent and E-vents 12 feet above grade
•            (2) 3/4" NPT Fittings for engine supply & return lines
•            Wire Fuel Tank Float Switches to Gen
•            C-Channel Generator Mounting Rails
•            Install Customer supplied Vibration Isolators
•            2" C-channel Inspection Beams beneath tank
•            FDEP UL Listed 5 Gallon Spill Box on fill port
•            75dBA @ 23' Average Free Field
•            175MPH Wind Loads
•            3" 4LB CU /FT. Rockwool Insulation
•            Reach-In style W/ LH and/or RH control panel & breaker
•            8 stage powder coat finish shall be applied to enclosure
•            Fuel tank shall be pressure tested prior to shipment
•            Standard (1) year warranty
•            30KVA Transformer 480-120/240V W/ Fused Disconnect Switch
•            AXI 150GPH Fuel Polishing System.
•            Access platforms. One Set per side of enclosure. Welded steel construction, powder coated black, removable handrails, stairs, anti-slip treads & decking & built to OSHA Standards.
•            Supply & install exhaust blankets for all internal parts of exhaust system.
OPTION B
Sub Base tank Only 
Troy Monson
Sales Engineer | Electric Power Generation
1500 Ziegler Drive North West  | Altoona, Iowa 50009-7200
515.957.3838 Office
515.314.7040 Cell
800.342.7002 Toll Free
515.957.3945 Fax