<!doctype html>
<html xmlns="http://www.w3.org/1999/xhtml" dir="ltr" lang="en-US">
<head>
<title>Request a Gensets Quote | Ziegler Caterpillar</title>
</head>
<body>
<p><strong>From:</strong> Troy Monson<br />
<strong>Company Name:</strong> Ziegler Caterpillar<br />
<strong>Email:</strong> troy.monson@zieglercat.com<br />
<strong>Phone:</strong> 5153147040</p>
<p><strong>Project Size:</strong> Small</p>
<p><strong>Project Description:</strong><br />
Generator Enclosure Request for Caterpillar C32-1250 </p>
<p>Please let me know if you are interested and if/when in 2023 you have production slots. Will need quick turnaround on this proposal.  </p>
<p>OPTION A<br />
175mph Wind Rating (Will be put in Florida Hurricane Zone A)<br />
5000 Gallon U.L 142 Sub Base Tank with FDEP (Florida Department of Environmental Protection)<br />
PE Stamped Drawings for the State of Florida<br />
Aluminum Panel Construction (marine environment) with powder coat exterior<br />
Fuel tank to have additional rubberized undercoat<br />
Use your equivalent as necessary<br />
I have the engine in stock </p>
<p>Weather protective enclosure<br />
•            3&quot; .125 Aluminum panel construction<br />
•            Enclosure frame 6&quot; Tall (Designed to remove entire enclosure for major service) Lugs only provided Per customer request or when enclosure ships to site separate<br />
•            Pitched Roof construction W/ Safety Lanyard tie off eye&#039;s spaced across entire roof<br />
•            Powder Coat Paint exterior Caulked seams<br />
•            Roxul 4lb UL Listed Acoustic/Thermal Insulation<br />
•            22GA Galvanized perforated interior liner<br />
•            Standard doors 36&quot;W x 72&quot;H<br />
•            Standard Door hardware with pad lock/key lock and hinges<br />
•            Stainless Steel spring loaded door hold back on every door<br />
•            Dripedge above all door openings<br />
•            Exhaust hardware for enclosure mounting<br />
•            Drip edge around exhaust opening (rain shield)<br />
•            Aluminum Gravity Radiator air discharge dampers<br />
•            Radiator vertical discharge air plenum W/ Screen &amp; 1 Access Door<br />
•            Aluminum Fixed intake louvers W/ Screen<br />
•            Document holder mounted inside enclosure<br />
•            Supply critical grade (Internal mounted) silencer &amp; exhaust system 120/240V 100A Load Center W/ Main breaker &amp; branch breakers<br />
•            (4) LED vapor tight lights W/ Guards (Includes: 2 GFCI receptacles &amp; 2-3 way light switches)<br />
•            4) Enclosure Doors (Two Per Side of Enclosure)<br />
•            IBC and Seismic Signed &amp; Approved Drawings by a PE for the state of Florida where the generator package will be installed Stainless Steel Door Hardware &amp; Hinges<br />
•            Stainless Steel Exterior Hardware<br />
•            UL 142 Secondary containment sub base tank<br />
•            Heavy gage side channels<br />
•            Mechanical Fuel level gauge<br />
•            UL/NFPA sized emergency vents<br />
•            2&quot; Standard working vent W/ Screen &amp; Rain Cap<br />
•            Low fuel level alarm (50%)<br />
•            Manual locking fill cap<br />
•            Rupture Basin alarm<br />
•            Lifting plates (2 Each Side-Min.)<br />
•            Prime and finish painted black) Electrical stub up area<br />
•            90% High Level Alarm<br />
•            Mount Generator on Fuel Tank<br />
•            Standard Fuel Lines<br />
•            2&quot; Quick Connect on fill port W/ Dust Cap<br />
•            2&quot; 95% Overfill Prevention Valve on fill port<br />
•            24V DC High Fuel Alarm Box W/ 90% Full Level Horn, Horn Re-Set Switch &amp; Reset Float Switch<br />
•            (2) 2&quot; NPT Spare Fittings<br />
•            Extend normal vent and E-vents 12 feet above grade<br />
•            (2) 3/4&quot; NPT Fittings for engine supply &amp; return lines<br />
•            Wire Fuel Tank Float Switches to Gen<br />
•            C-Channel Generator Mounting Rails<br />
•            Install Customer supplied Vibration Isolators<br />
•            2&quot; C-channel Inspection Beams beneath tank<br />
•            FDEP UL Listed 5 Gallon Spill Box on fill port<br />
•            75dBA @ 23&#039; Average Free Field<br />
•            175MPH Wind Loads<br />
•            3&quot; 4LB CU /FT. Rockwool Insulation<br />
•            Reach-In style W/ LH and/or RH control panel &amp; breaker<br />
•            8 stage powder coat finish shall be applied to enclosure<br />
•            Fuel tank shall be pressure tested prior to shipment<br />
•            Standard (1) year warranty<br />
•            30KVA Transformer 480-120/240V W/ Fused Disconnect Switch<br />
•            AXI 150GPH Fuel Polishing System.<br />
•            Access platforms. One Set per side of enclosure. Welded steel construction, powder coated black, removable handrails, stairs, anti-slip treads &amp; decking &amp; built to OSHA Standards.<br />
•            Supply &amp; install exhaust blankets for all internal parts of exhaust system.</p>
<p>OPTION B</p>
<p>Sub Base tank Only </p>
<p>Troy Monson<br />
Sales Engineer | Electric Power Generation<br />
1500 Ziegler Drive North West  | Altoona, Iowa 50009-7200<br />
515.957.3838 Office<br />
515.314.7040 Cell<br />
800.342.7002 Toll Free<br />
515.957.3945 Fax</p>
</body>
</html>