I am seeking a proposal for a Motorola Specd shelter delivered to Avimore in Idaho. 
A. DESIGN SPECIFICATIONS
1. Radio Site Shelter: Type C shelter specified to meet or exceed current
R56 “Standards and Guidelines for Communication Sites” and must include, but
not be limited to, the following elements:
• Building Size: At a minimum, 12’ W x 25’ L X 10’H
• 10’ Interior Partition and Over Size Door to Generator Room
• Type C shelter, pre-wired and 24” wide cable trays positioned 12”
below the ceiling level and allow for placement of a 7’ equipment rack
below with no more than 6” of spacing from top of rack to bottom of
cable trays.
• Exterior Walls, Roof: Concrete 2 hr. fire rated, Ballistics tested for
UL-752
• Insulation: Walls: R-11, Ceiling: R-19