SPECIFICATIONS:
•	Floor Load:	300 psf
•	Roof Load:	150 psf
•	Walls:	150 mph

BUILDING SIZE:
•	Outside (Nominal):	12’-0” W x 30’-0” L x 9’-0” H
•	Outside (Shipping):	12’-4” W x 30’-6” L x 9’-6” H
•	Estimated Module Weight:	95,000 lbs.

SHELL:
•	Floor:	5 3/4” Solid concrete floor
•	Walls:	4” Solid concrete
•	Roof:	Solid concrete 4” at eave and 5 1/2” at ridge
•	Design:	Step-joint design
•	Tie down:	(4) Tie down plates
•	Bolts:	Painted bolts to replace lifting lugs
•	Concrete:	5000 psi lightweight concrete
•	Reinforcing:	Steel #4 and #6 bars, 60,000 psi (Grade 60 ASTM-615)
•	Ratings:	Exterior walls 2-hour fire rated
•	Ballistics:	Tested for UL-752 Level 4 (HPR-30.06 point blank)
•	Ice Bridge	(1) 12’ x 30’ Galvanized ice guard installed above building

EXTERIOR FINISH:
•	Walls:	Washed exposed aggregate and sealed
•	Roof:	Trowel surface and sealed, broom finish

INTERIOR FINISH:
•	Floor:	Covered with 1/8” x 12” x 12” white commercial tile and a 4” base cove
•	Interior Walls:	3/4” APA Rated OSB covered with white embossed fiberglass
reinforced plastic (FRP)
•	Ceiling:	3/4” APA Rated OSB covered with white embossed fiberglass reinforced plastic (FRP)

INSULATION:
•	Exterior Walls:	R-11 Rigid Polyisocyanurate Insulation
•	Ceiling:	R-19 Rigid Polyisocyanurate Insulation

DOORS:
•	Quantity/Size:	(1) 3\'x7\' exterior steel door with passage hardware
(1)	4\'x7\' exterior steel door with passage hardware
•	Door Type:	18 ga. Insulated metal door, painted to match exterior finish
•	Frame Type:	16 ga. Painted galvanized metal frame
•	Lock Hardware:	Latch guard for electric strike, HES 150
•	Electric strike	4500c w/smart Pac
•	Mortise Lock	Small format IC, 7-pin core
Mortise panic w/security plt &amp; mortise cyl. (9500 Series NPT03M)
•	Hinges:	Ball bearing hinges w/non removable pins, 26d
•	Door contact	Hager
•	Weather Strip:	Magnetic weather stripping
•	Threshold:	Saddle type threshold, mill finish aluminum
•	Door Sweep:	Neoprene style, mill finish aluminum
•	Anti-pick Plate:	Latch Guard
•	Hold Back:	(1) Hydraulic closer w/hold-open arm
•	Drip Cap:	Drip cap, mill finish aluminum
•	Door Awnings:	To extend 12” beyond the doors and key access pad; 42” deep
•	Card Reader with Keypad	HID PROXPRO 5355 and DPS Telecom ECU LAN

AIR CONDITIONING / HEATING:
•	Quantity/Type:	(2) Wall-Mount
•	Brand/Size:	Bard 2-Ton with Economizer
•	Controller:	Bard MC4002-B
•	Voltage:	120/208V 1 phase
•	Description:	24,000 BTUs/each with 5kW heat
•	Ventilation:	(1) Exhaust fan with thermostat and damper
(1) 12”x12” louver with filter box and 30%, 2” pleated filter
GENERATOR ROOM:
•	Generator:	(1) 40KW Generac LPV genset wired for 120/240 VAC SP, 60 Hz
•	Ventilation:	(1) Ventilation package for generator room, intake with filter,
exhaust, 12” fan, outside hoods and thermostat
•	Heat:	(1) Baseboard heater for generator room
•	Conduit:	All conduit will be at least 6” above floor
•	Floor Drain:	(1) 3” floor drain located between door entrance and generator
•	Patch Panel:	(1) Cat 5 cable patch panel for up to 4 connections
•	Wall Penetration:	3” penetration for additional wiring access to main room at cable tray
ELECTRICAL:
•	Service:	120/240 volt single phase
•	Main Panel:	(1) 200 amp, EEE integrated load center TSA200-2HH3FF-234S-3309P01VL
•	Disconnect	(1) 200A single phase service disconnect switch
•	Generator Connector	(1) Intersect ICL-1P-R
•	Sensors:	(1) Occupancy Sensor Switch
•	Wiring:	To include sufficient slack for trouble shooting To be labelled correctly
•	Wall Receptacles:	(8) 120V 20A Quad Receptacles
(1) 120V 20A outdoor GFI receptacle
•	Ceiling Receptacles	(10) Twistlock Receptacles
(8) Additional 20 amp twist locks above each row of racks ((2) Above each rack)
•	Grounding:	Interior ground halo with (3) master ground bars per CSI specification
•	Bonding:	TelcoFlex IV #6
•	External weather box:	With lightning protection for PoE

Note: Wiring to be labeled with slack for troubleshooting. Equipment mounted to panel board is to have adequate space for access. Cable ways to be large enough for growth.
All electrical conduits to be galvanized EMT and fittings to be compression type. No set screw type permitted. Horizontal runs of EMT to be installed 7’-6” aff whenever possible. All flex conduit to be seal tight type. Wire-way, conduit and/or drop box will be properly de-rated for compliance with current adopted edition of NEC code.

INTEGRATION:
•	(7) B-Line SB5060XUYZ relay racks
•	(1) AR-400-48VBC-X (Contains the items below)
o	(1) La Marche LMP-200A-48V power system
o	(4) Rectifier module 50A/48V (DCR50)
o	(6) Load breaker 100AMPS (3 A&amp;B PANELS AT 100A EACH)
o	(2) Load breaker 60AMPS
o	(1) Load breaker 40 AMPS (Inverter)
o	(4) Load breaker 20AMPS
o	(1) LTI2 Pro Inverter 48V TO 1KVA (LTI2-1K-48V-A6-21X) (Bond ground and neutral wire at 120 VAC output)
o	Battery Disconnect Breaker BBP19-48V-1-250A
o	(1) 19\&quot; X 7\' relay rack (P3-RR-P040)
o	(1) Mount wire test (MWT 1)

•	Panel #1
o	(1) Split bus distribution 7 \&quot;A\&quot; &amp; 7 \&quot;B\&quot; positions (BPV19-48V-14R-X)
o	(10) P4-ALMLB-20D1B Breakers
•	Panel #2
o	(1) Split bus distribution 7 \&quot;A\&quot; &amp; 7 \&quot;B\&quot; positions (BPV19-48V-14R-X)
o	(10) P4-ALMLB-20D1B Breakers
•	Panel #3
o	Split bus distribution 7 \&quot;A\&quot; &amp; 7 \&quot;B\&quot; positions (BPV19-48V-14R-X)
o	(10) P4-ALMLB-20D1B Breakers
•	Battery Plant:
o	(1) East Penn 24AVR95-17 battery (48VDC)
o	(4) #2 TelcoFlex IV cables in parallel between battery disconnect breaker and the battery
o	(4) #2 TelcoFlex IV cables in parallel between the battery and the DC plant return buss
o	(4) #2 TelcoFlex IV cables in parallel between battery-disconnect breaker and DC plant

•	DC Wiring
o	(350’) #2 TelcoFlex IV (Black)
o	(350’) #2 TelcoFlex IV (Blue)

•	Leviton Package o
o	(17) - E2X1A-S48-48 Port Angled Patch Panels
o	(44) - Copper Cassettes
o	(32) - E2XHD-BNK-Cassette Blanks
o	(17) - E2XHD-COV-Angled Panel Covers
o	(17) - E2XHD-CMB-Rear Cable Managers
o	Leviton Cables per LAN Cable Schedule
•	12VDC DC-DC system
o	(1) Wilmore 1502-48-13-30 DC-DC Converter
o	(1) LaMarche BPKR19-12-L-18RN 12VDC Breaker Panel
o	(4) 5 Amp Load Breakers
o	(4) 20 Amp Load Breakers

LIGHTING:
•	Interior:	(10) 4 ft. LED fixtures, wraparound 360 Degree Motion Sensor:
•	Exterior:	(2) Exterior LED fixture
•	Flood Lights:	(4) LED flood lights with motion detector and switch
•	Wall Switch:	(2) 20A Two-way switch

CABLE MANAGEMENT:
•	40 linear feet of 24” cable ladder rack (will extend to each corner of radio room)
•	(4) Single 4” Cable Entry Ports (upper corners of radio room)
•	(1) 10-hole waveguide entry panel with 4” ports
•	(1) Cable trapeze
•	Rack overhead bracing and ladder rack support to CSI specifications
•	(5) Panduit PR2VD006 Vertical Cable Managers

ALARMS:
•	Alarm package	Wired to type 66 punch block including door, high/low temp, smoke,
Humidity, CO2, and power fail with remote monitoring
•	Wiring:	Cat 5 cable to the 66 block. (cat 5 cable to have cable pairs with primary color and white stripped primary color. Main jacket to have label for identification).
25 pair connectorized cable from NetGuardian 420 to 66 block.
•	Cat5 network box:	Mounted with two connections back to main switch area.
•	Small panel board:	Mounted on wall for interface options with 66 block/25 pair wiring
back to main panel board.
•	Netguardian:	D-PK-NG420-12070.00001-NetGuardian-BNSF, Dual -24/-48V,
NIC, T/B, HA, 1-plug, xFLSH, 4ALG
•	Temperature/Humidity	(2 each) D-PK-DSNSR-12002.00101 - DPS Sensor Node, Temp &amp;
Humidity G2, Alum, RoHS
•	Door Sensor:	To be located at top of door frame on opening side

SAFETY:
•	(1) Battery safety kit, #3ZM54
•	(1) Eyewash station, #4GA89
•	(1) First aid kit, #4EY88
•	(1) 10LB, CO2 fire extinguisher

MISCELLANEOUS:
•	Binder Holder:	(1) Wall pocket for storage of documentation
•	Drawings:	(1) Complete set of shop drawings for review
(1) Foundation drawings
(1) Stamped prints upon approval
(1) Folding Worktable
(1) Fire retardant Telco Board

•	Shelter to be delivered to 89445

