I would like to seek for a quote to have Fibrebond provide a rough order of magnitude quote for fabrication and delivery of a new shelter for each of (4) telecom sites located in Spokane County WA.  The criteria of the shelter would need to meet the following:


SPECIFICATIONS: 
•	• Design Floor Load: 250 PSF 
•	• Roof Load: 120 PSF. 
•	• Walls: 120 MPH 
•	• Wind Load: Vult 115 Nominal 89MPH 
•	• Ground Snow Load 80 PSF 
•	• Seismic As required for location 
•	• Seismic Design Category As required for location 
•	• State Process State of Washington Gold Seal Process 
•	• PE Stamped Drawings State of WA PE stamped drawings for Building permit 

BUILDING SIZE: 
•	• Outside (Eaves): 10’-4” W x 20’-4” L x 10’-8” H. 
•	• Estimated Module Weight: 56,000 lbs. 

SHELL: 
•	• Floor: 5 3/4” Solid concrete floor. 
•	• Walls: 4” Solid concrete. 
•	• Roof: Solid concrete 4” at eave and 5 1/2” at ridge. 
•	• Design: Step-joint design. 
•	• Tie down: (4) Tie down plates. 
•	• Bolts: Painted bolts to replace lifting lugs. 
•	• Concrete: 5000 psi lightweight concrete. 
•	• Reinforcing: Steel #4 and #6 bars, 60,000 psi. 

(Grade 60 ASTM-615). 
•	• Ratings: Walls to 2-hour fire rated. 
•	• Ballistics: Tested for UL-752, (HPR-30.06-point blank range, excluding door and other equipment). 

EXTERIOR FINISH: 
•	• Walls: Washed exposed aggregate and sealed. 
•	• Coatings Painted exterior trim with Epoxy Coating 
•	• Roof: Trowel surface and sealed, broom finish. 

INTERIOR FINISH: 
•	• Floors: Covered with 1/8&quot; x 12&quot; x 12&quot; white commercial tile and a 4&quot; base cove. 
•	• Interior Walls: 1/2&quot; APA Rated OSB covered with a white, embossed fiberglass reinforced plastic (FRP). 
•	• Ceiling: 1/2&quot; APA Rated OSB covered with a white, embossed fiberglass reinforced plastic (FRP). 

INSULATION: 
•	• Exterior Walls: R-19 Rigid Polyisocyanurate Insulation. 
•	• Ceiling: R-19 Rigid Polyisocyanurate Insulation. 

DOORS: 
•	• QTY / Size: (1) 3670 Door – RHR Swing 
•	• Door Type: 18 ga. Insulated Door, painted to match exterior finish. 
•	• Frame Type: 16 ga. painted galvanized metal frame 
•	• Lockset: Card reader/Keypad with remote access capability – remote monitoring/system is by others 
•	• Keys Card reader entry access cards 
•	• Hinges: NRP - SS hinges 
•	• Weather Strip: Magnetic Weather Stripping 
•	• Threshold: Saddle type threshold, mill finish aluminum 
•	• Door Sweep: Neoprene style, mill finish aluminum 
•	• Anti-Pick Plate: Latch Guard / or equal. 
•	• Door Closer: Closer and locking hold open mechanism 
•	• Drip Cap: Aluminum drip cap full width of door. 

ELECTRICAL: 
•	• Service: 120/240V 200A- 1PH 
•	• Surge Suppression: (1) – Transtector #1101-808MM-1/Imax with metal housing, MOV protection, single phase power; 120/240 Split phase 160Ka MOV 
•	• Surge Suppression (1) Transtector #1108-808-1/IMAX 120T with Fiberglass Housing, Silicone Avalanche diode/MOV protection, Single phase Power, 120/240 Split phase, 138 VAC L-N 
•	• Automatic Transfer Switch Excluded 
•	• Manual Transfer Switch Excluded 
•	• External Appleton Plug Excluded 
•	• Main Breaker Panel: (1) 200A Distribution panel – 42 Space, 
•	• Branch Circuits (8) Isolated rack Outlets Simplex 30 A L520 R 
•	• Duplex Receptacles: (6) Wall Mounted service outlets 
•	• GFI Receptacles: (1) Exterior GFI specification grade receptacle 

Note: all electrical conduits to be galvanized EMT and fittings to be compression type. No set screw types permitted. Horizontal runs of EMT to be installed 7’-6” aff whenever possible. All flex conduit to be seal tight type. Wire-way, conduit and/or drop box will be properly de-rated for compliance with current adopted edition of NEC code. 

LIGHTING: 
•	• Interior: (8) 4 ft., 2 bulb, LED Interior Lights. 
•	• Exterior: (1) LED exterior light, switch controlled 
•	• Occupancy Sensor (1) Energy savings occupancy sensor with temp override 
•	• Wall Switch: (2) 20A Single pole switch, 

AIR CONDITIONING/HEATING: 
•	• Quantity: (2) 3 Ton HVAC Units; 11 EER 
•	• Description: 36,000 BTU units with integrated 5kW heat strips, time delay anti-short cycle timer, high- and low- pressure switch, low ambient control, and a one- year parts and labor guarantee. 
•	• Temp. Control: (1) Lead Lag Master controller with alarms. 
•	• Passive Cooling (1) 12” wall mounted exhaust fan, with mechanical exhaust and intake louvers, and thermostat control 

ALARM SYSTEM: 
•	• Terminal Block: (1) Dry terminal, 66 blocks with cover. 
•	• Intrusion: (1) Door alarm. 
•	• Temperature: (1) High. 
•	• Temperature: (1) Low. 
•	• Smoke: (1) Photoelectric smoke detector. 
•	• Cameras (2) Camera systems 1 internal 1- external 
•	• Alarms and cameras are prewired to a 66-point dry terminal punch block from the point of alarm. Remote monitoring is excluded and by others 

CABLE ENTRY: 
•	• Cable Entry Port: (1) Microflect Waveguide 3 x 4 -12 Hole cable entry port. 
•	• Wall Ports (1) Fiber and electrical as required for the site 
•	• Fiber entry Can be provided- as a floor port, or external NEMA 3R wall mounted box 

CABLE LADDER: 
•	• 12” Wide: (50) LF of 12” cable ladder, 8’-0” aff to the bottom of the cable ladder 
•	• 6 “Wide: As required for cross connections and vertical risers 
•	• Seismic Racks (12) 23” racks in two rows with seismic bracing 

GROUNDING: 
•	• Halo System: No. 2 AWG Bare, stranded copper wire around inside perimeter of building/rooms as shown on supplied plans with each end lugged to master ground bar, Single point system 
•	• Ground Bars: (1) 24” x 4” x 1/4” ground bars interior with insulators, mounting brackets, and 15 ft of #2 tinned solid AWG wire coiled for connection to earth ring through 1” pvc cast in wall. 
•	• Bonding Bonding of individual components to the halo ground including HVAC units, grilles, electrical panels, door, boxes over 4’x4”, cable tray and racks 

MISCELLANEOUS: 
•	• Telco Board: (1) 3’-0” x 4’-0” plywood covered with FRP 
•	• First Aid Kit: (1) First aid kit, North 4EY92 
•	• Eye Wash: (1) Eye wash solution, wall mounted, North 1KW79 
•	• Fire Extinguisher (1) 20 LB ABC Fire extinguisher 
•	• Binder Holder: (1) Wall pocket for storage of documentation 
•	• Stamped drawings (3) sets of PE stamped drawings 
•	• Leveling (1) packet of ship loose leveling shims 
•	• Foundation design Stamped engineered foundation drawings from the provided soil sample reports 

Thank you,

Richard B. Hall, AIA, NCARB
Senior Architect
LDC, Inc.
425-802-1219
rhall@ldc.corp.com

PS:  Please have sales contact me today 425-802-1219.